Swamp Cooler start up.
Camino Rojo SANTA FE, NM
Technician turned gas to boiler off. Conducted a gas leak test. No gas leak. Conducted a water heater inspection. First CAPP plan visit. 3 More to go.
Plaza rojo SANTA FE, NM
Technician performed a swamp cooler start up.
Tano Norte SANTA FE, NM
Swamp Cooler Start up.
Vista Precioso SANTA FE, NM
Technicians performed a duct cleaning. Also ran air supply to furnace.
Paseo de la Conquistadora SANTA FE, NM
Inspection of a gas fire place.
Calle Ventoso West, Santa Fe, NM SANTA FE, NM
A/C start up under Capp plan, new capp plan renewal, customer denied surge protector. Note: Customer will like to have a drip leg installed on the boiler during her fall visit.
Calle Perezoso SANTA FE, NM
Proposal for installation of a Trane XR16 was given to the customer.
W. Alameda St. SANTA FE, NM
Technician installed surge protector on a Fujitsu outdoor unit.
Entrada De Gonzales SANTA FE, NM
FIxed a leak on the Fujitsu minisplit, installed 3 surge protectors as well.
B Ranch house rd SANTA FE, NM
Replacement of a zone valve body and bleed the system. (Boiler and the 6 zone).
B Barton Rd SANTA FE, NM
We located and repaired several leaks in the gas line, performed pressure test and had it inspected. Installed a Trane XR80 80,000 BTU up flow furnace up-flow system. This system carries a limited 20 year heat exchanger warranty, 10 year limited parts warrant, and a 10 year limited workmanship warranty. Rich has provided professional discounting. Trane XR 80 80,000 BTU upflow furnace including materials and labor.
Mesa Vista SANTA FE, NM
Installation of a Surge Protector
West Sand Sage Santa Fe, NM SANTA FE, NM
Technician replaced gas valve on Cozy furnace.
Calle Margarita SANTA FE, NM
Replace customer supplied thermocouple. $125 per hour. Need to return to install check valve and 1/2 inch ball valve also order body for pilot assembly.
Rito Guico SANTA FE, NM
Performed inspection on Bryant system unit is a 1995 model was not derated for high-altitude. Performed carbon monoxide test had one part per million coming out of the vent and four ppm's in the mechanical room this may be from the water heater can't tell. Also checked run capacitor system is reading 4.4 mfds. Hot surface igniter is a Norton igniter should be reading between 40 and 70 ohms actual reading was 88 ohms. Flame sensing diode fluctuated between 3.7 and 4.2. Parts per million test in stack reached 700 ppm which is very very high. I recommended to customer not run the heating system that they should consider an alternative source of heat I do not want to read tag because of fear of the piping. He is going to talk to his wife to figure out what the next step would be. I also gave customer options in regards to the water heater the water heater is also the original system quote for 1600+ tax however if a furnace is installed we were reduced the amount to 1200+ tax be advised I did not check the PRV valve this will have to be done at the time of installation.
Casas de Milagros SANTA FE, NM
Installation of Surge Protectors.
Camino Capitan SANTA FE, NM
Found two defective old style Honeywell could not replace due to stuck gasket. Water spraying out the sides when tech attempted to do so. Will provide an estimate on options.
Governor Dempsey Drive SANTA FE, NM
Shut down pn swamp cooler extended vent on furnace.
Calle la Resolana SANTA FE, NM
Winterized the swamp cooler, Also checked water heater pointed out she needed to hard pipe TMP and expansion tank need to be installed.
Govenor Mechim SANTA FE, NM